- Model NO.: XBD-GDL
- Type: Self-Starting Diesel Generator
- Stroke: Four Stroke
- Output Type: AC Single Phase
- Specification: CE
- HS Code: 84101330
- Main Advantage: Xbd-Gdl Vertical Multistage Fire Pump
- Installation Method: Portable
- Cooling Method: Water Cooling
- Trademark: Liansheng or OEM
- Origin: Shanghai, China
Products Name:Vertical Multistage Fire water pump
XBD series fire pump is our company according to the requirements of the actual needs of the market for fire pump and its special use, development of new fire protection product development in strict accordance with the new "GB6245-2006" standard of fire pump. By the national fire equipment quality supervision and testing center of detection, the performance indicators have reached or exceeded the standard requirements, and obtained the national fire products certification.
1. Fire hydrant fixed fire protection system of XBD series fire pump is mainly used for various enterprises and institutions, engineering construction, high-rise buildings and fire extinguishing system, automatic sprinkler system.
2. It can deliver 100 Degrees Celsius not containing solid particles of water and physical and chemical properties similar to water medium.
3. It can be used for fire fighting, life, production sharing water supply system and construction, municipal water supply and drainage.
1, the weight of pipe shall not be installed in the pump body, otherwise easy to damage the pump;
2, pump and motor are the overall structure, the factory has been corrected by manufacturers, so the installation does not need to be adjusted, so the installation is very convenient;
3, the installation must tighten the anchor bolts, and every certain time to pump check to prevent it from loosening, violent vibration and impact on pump performance in order to avoid the pump start;
4, in order to maintain convenient and safe use, a regulating valve and a pressure gauge installed near the outlet installed in the export pipeline pump, for the high lift pump, in order to prevent water hammer, should also be a check valve installed in the outlet valve to prevent a sudden power failure, before the loss of power accident, so as to ensure the pump run in the best condition;
5, for a suction pump applications, shall be fitted with a valve, and the inlet pipe should not be too many corners, and there shall be no leakage Water Leakage phenomenon, so as not to affect the suction pump capacity;
6, in order not to make the impurities into the pump and plug flow affects the performance, the pump inlet filter should be installed in the front;
7, should be regularly (usually 15 days) trial operation of pump, the running time is about 1 hours, in order to prevent emergency axle card death cannot run...
Instructions for use
Before the start of:
1, hand rotation coupling, rotor parts should be no blocking phenomenon.
2, open the inlet valve, the exhaust valve so that the water filled in the pump cavity, then close vent valve;
3, to move the motor, determine the shift is correct;
1, open the inlet valve, close the outlet pipeline valve.
2, switch on the power, when the pump speed to normal, re export pipeline valve is opened, and adjust to the desired operating point;
3, to observe the pump running any abnormal situation, such as the abnormal situation should immediately stop checking, treatment after operation;
Stop the car:
1, gradually close the exit valve, cut off the power supply;
2, close the inlet valve;
3, such as the environment temperature is below 0 Centigrade, should take measures to keep warm.